A Fishtown resident was concerned about water leaking from their main electrical panel. They contacted Lauterborn Electric to evaluate and provide an estimate to remedy the Issue. The main 100 AMP panel was installed by anther electrical contractor less than 2 years ago. When we stepped outside to check where the leaking was coming from, we found the problem. The 100 AMP main service cable was frayed to the point where exposed strands were showing. Water was easily penetrating the cable into the meter socket, down the cable and into the main panel. Lauterborn Electric Installed a new 100 AMP service cable sleeved in PVC for added protection. The meter socket was corroded and also replaced and the problem was resolved. For all your electrical needs contact your Philadelphia Electricians Lauterborn Electric. Click Images to Enlarge.