The new home owners of this property received an inspection report stating that the main panel had several violations including some double tapped breakers.
The original service entrance cable had water dripping into the meter socket causing some corrosion to occur. The grounding of the system was also inadequate.
These images below depict the condition of the panel as seen by the home inspector.
If you are in the process of purchasing a home and have a home inspection that needs clarification, contact your licensed electrical contractor at Lauterbornelectric.com