Lauterborn Electric was called to a home in the Fishtown neighborhood of Philadelphia. The home owner had been doing work on their property without proper permits and was caught by the department of licenses and inspections of the city Philadelphia. They were gutting the property and redoing the entire house. The pictures show what we saw as we entered the property. Wiring was not done to code, electric metallic tubing (EMT) was running and multiple wires were stuffed into them which is against code. This condition can cause overheating and potential hazard. The bathroom was tapped off from a kitchen circuit which is against code. No smoke detectors were run which is a safety issue. Junction boxes were all over the place in what would be drywall covered ceilings and also behind where kitchen cabinets will be. Junction boxes must be accessible in case of a connection going bad. The lack of electrical code knowledge was obvious on this site. The customer was trying to save a buck but now has wiring throughout that no licensed electrician will sign off on. For all your electrical needs contact your Philadelphia Electrician Lauterborn Electric. Click Images to Enlarge.
- The main electrical service cable is frayed or the strands inside the main cable are exposed. This condition leads to water penetrating the cable and compromising the meter socket or main panel.
- The main electrical panel is outdated. Many older brand panels and breakers such as Push-A-Matic or Federal Pacific have been condemned due to their non-tripping or overheating breakers creating a potential electrical hazard.
- You need additional power. Most homes main services are rated at 100 amps, if additional appliances are added to the service such as an electric oven, central air, or electric hot water heater the 100 amp service might be insufficient and a 200 amp service would be needed.
- You are adding circuitry and your main panel is undersized. Many older homes still have their original 12 circuit panel, and if appliances or dedicated lines are added installing a larger 20 or even 30 circuit panel would allow for the additional circuits
- You have fuses and want to upgrade to breakers. The older homes throughout Philadelphia originally had fuse boxes instead of breakers. This older method is outdated and many have been compromised by oversizing fuses or even installing pennies to allow the circuits to keep operating. Both of these methods are dangerous and can create a potential electrical fire hazard.
If your main electrical service resembles any of these images, feel free to contact your licensed Philadelphia electricians Lauterborn Electric for a free estimate. Click Images to Enlarge.
During our travels to the many homes and businesses we see many poor or in some cases dangerous electrical installations. Running extension cords and data lines across floors or under a rug is a very common occurrence. Not only does the wiring possess a tripping hazard, but worse the wiring can overheat creating a potential electrical fire. The images show several wiring installations in a retail setting that shows exactly how not to properly run data and electrical lines. In locations where counter areas have no access to walls to allow for wiring Lauterborn Eclectic recommends the installation of a power and data pole. This ensures the safety of the people walking around the area while also protecting the wiring. For all of your electrical needs contact your licensed Philadelphia electrician Lauterborn Electric. Click Images to Enlarge.
Panel labeling is sometimes a tedious task for electricians especially if the house is not new construction. A panel should be labeled on a separate piece of paper or on the panel cover. Some electricians leave extra wire covering inside of panels to mark each line. This enhanced the danger of a trouble shoot situation we had recently. A customer called and said his breaker is tripping over and over again and he smells burning in the panel. The problem was a loose connection on the breaker. The wire was beginning to burn itself bare and the pictures show the labeling on the wire creating an even bigger hazard situation. The solution was to change the breaker which was extremely hot and cut the wire back to the part that was not damaged to reinstall on a new breaker. For all of your electrical needs contact your licensed Philadelphia electricians Lauterborn Electric. Click Images to Enlarge.
Lauterborn Electric has been very busy lately rewiring multiple residences all over the City of Philadelphia. Many properties in Philadelphia still have the original wiring dating as far back as the 1920’s This rewiring requires us to take out all of the old wiring which includes old cloth wire, BX wire and knob and tube wire. These types of wiring are all outdated and can cause a hazardous situation. Knob and tube wiring is ungrounded and usually is falling apart due to the many years of use and overuse. BX is metal encased wire that uses the metal casing as a ground. However these metal casings become corroded and oxidized overtime causing the loss of grounding in devices. This is dangerous to a homeowner because a three pronged outlet can become ungrounded. We are making our way through the city replacing as much of this old wiring as possible. For all of your electrical needs contact you licensed Philadelphia electricians Lauterborn Electric. Click Images to Enlarge.
A repeat customer in Northern Liberties recently decided to have under cabinet lights installed. After a brief consultation we came to the conclusion to use three separate LED Light strips. Wiring was installed to two locations and the third strip was connected with a joiner piece. We also installed an outlet above the cabinet for a speaker. The customers are very happy. They have given us a review on yelp and google and also put us on Instagram. The pictures show the final result. For all your electrical needs contact your Philadelphia licensed electricians Lauterborn Electric. Click Images to Enlarge.
Lauterborn Electric recently put the finishing touches on a project in the Point Breeze section of Philadelphia. The job included a total remodeling of all bathrooms and kitchen. Customer supplied fixtures gave this property a very unique look. LED recessed lighting was used throughout the living room, dining room and kitchen. Two LED recessed lights were installed in the master bathroom shower. The pictures show the finished product. For all of your electrical needs contact you Philadelphia licensed electricians, Lauterborn Electric. Click Images to Enlarge.
The City of Philadelphia has made it a requirement for all workers directly performing construction or demolition to complete OSHA 10 safety training. Lauterborn Electric recently fulfilled that requirement. Each construction company must also have an OSHA 30 supervisory employee. OSHA was created to assure safe and healthful working conditions for working men and women by setting and enforcing standards and by providing training, outreach, education and assistance. Clean working areas free from clutter or debris, properly secured openings on floors including guard rails to prevent falls, and safe working clearances from the edges of an elevated area are some of the conditions that OSHA brings to light to help prevent job related injuries or hazards. Images shows examples of potentially hazardous working conditions. Lauterborn Electric will continue to expand on safety practices on job sites to create a safer working environment. For all of your electrical needs contact your licensed electrician Lauterborn Electric.
Lauterborn Electric has been busy running numerous projects throughout the city of Philadelphia. One of our recent customers from the Queen Village section of the city found us on Yelp and reached out for a free estimate, which we gladly provided. This 100 AMP service is an example of what we do – provide safe, quality electrical services to our customers. We ensure that our installations are not only safe but also visually appealing and, of course, up to the latest electrical codes. Squaring and leveling the equipment and providing additional sleeving of the service cable for protection are just a couple examples of added value that we routinely provide. Our number one goal is to provide great electrical service to all of our customers. For all of your electrical needs contact your licensed Philadelphia Electrician Lauterborn Electric. Click Images to Enlarge.
We were recently called to a retail store to correct an issue with an overloaded circuit that was tripping a breaker. When we arrived we found the overloaded circuit was only half of the story. A coffee maker, mini fridge and cable box were plugged in with the help of an extension cord that was being run over the top of a doorway. There was also a mess of cords that created a tripping hazard. The solution was simple. We installed a new outlet powered by a dedicated circuit in a place where no more extension cords would be necessary. For all of your electrical needs contact you licensed electrician Lauterborn Electric. Click Images to Enlarge.